On 1/26/2023 I arrived on site and began recovering the refrigerant from the system. After I recovered the refrigerant. I removed the filters in the liquid line and replaced the bad compressor with a new compressor installed new filter dryers on the liquid line. I pulled a vacuum on the system at that point I found a leak on the suction line going into the store fixed the leak and pulled another vacuum on the system and then charge the system with 404A. The thermostat was bad inside the cooler, so I replaced it with a new one and moved the position of the bulb to the back wall in Austin Texas.
Near Guadalupe Street Austin, Texas 78705
Check out the Areas We Serve and jobs we are doing by clicking: https://prorefrigerate.com/areas-we-serve/
Leave a comment