On 12/23/2022 I added 4 lbs of 407a to clear the sight glass, once cleared I started a leak search on the condenser. I have found that the liquid service port was leaking Freon they both suction and liquid didn’t have caps, I put caps on to fix the leak. Then placed all the coverts back and added a lot of screws that were missing. Then o started a leak search at the evaporator I didn’t find leak there. Noticed that the cooler thermometer was not working so I replaced an aftermarket thermometer. The drain insulation were broken so I replaced it with foam tape. Some pictures attached to this invoice Cooler working from 35° to 40° in Round Rock Texas.
Near Gattis School Road Round Rock, Texas 78664
Check out the Areas We Serve and jobs we are doing by clicking: https://prorefrigerate.com/areas-we-serve/