On 3/17/2023 I arrived on site, installed a new contactor and put the new fuses in found that the site glass was flashing. I found a leak on a discharge Schrader core, replace the Schrader core and found a leak on the power hose to the low-pressure switch. I fix the leak on the power hose and added 3 pounds of 404a to the system I leak checked again didn’t find any leaks in Buda Texas.
Near South Main Street Buda, Texas 78610
Check out the Areas We Serve and jobs we are doing by clicking: https://prorefrigerate.com/areas-we-serve/
Leave a comment