On 8/10/2023 Found ref leak on outlet of the TXV (Cracked copper line on the distributor tube, not the TXV outlet joint.) After repairing ref leak I checked to see if it pumps down correctly. System does not use a solenoid valve. Shut the king valve and found that the compressor stays on when pumped down into a vacuum. Monitored thermostat reach 17*f before departure in Leander Texas.
Near S Bagdad Rd Leander, Texas 78641
Check out the Areas We Serve and jobs we are doing by clicking: https://prorefrigerate.com/areas-we-serve/