Found a leak on the system on the king valve at the condenser between the compressor and the condenser. Removed and replaced the bad valve that was leaking and also replaced the filter dryer. I added 14 pounds of 448 a to the system until the eyeglass cleared monitored the system to make sure it gets down to temperature on 1/9/24 in Round Rock Texas.
Near Oakmont Drive Round Rock, Texas 78665
Check out the Areas We Serve and jobs we are doing by clicking: https://prorefrigerate.com/areas-we-serve/