On 2/15/2023 Found low pressure control stuck open with a suction pressure above 100psi. Forced compressor on by adjusting cut in to vacuum pressures. Cut out pressure was damaged regardless of what I set it to. Replace LPC. Confirmed proper pump down operation after replacing LPC. Monitored System A back bar drop to correct temp in Georgetown Texas.
Near West 2nd Street Georgetown, Texas 78626
Check out the Areas We Serve and jobs we are doing by clicking: https://prorefrigerate.com/areas-we-serve/
Leave a comment