On 4/17/2023 I arrived on site and found that the cooler was a 60 degree and the expansion valve was frozen up expansion valve and not adjusted. I replaced the expansion valve and the system started to work properly I had. To add 1 pound of 407a due to replacing valve. I watched the system drop in temp. I tested to make sure the system pumps down and that the defrost clock works in MANOR Texas.
Near Shadow Glen MANOR, Texas 78653
Check out the Areas We Serve and jobs we are doing by clicking: https://prorefrigerate.com/areas-we-serve/
Leave a comment