On 11/29/2022 I arrived on site and cleaned the coils. I also found that there was a leak on one of the king valves, causing the freezer to not work properly. I fix the leak and had to adjust the super heat. While I was doing that, I found that the shield to the top of the box was not working properly and put new foam tape to help seal it better. I turned the freezer on, found that it would not cycle off when it getting to temp. I installed a new t stat and making sure it cycles on and off. I set the difference for 5 degrees. The set point to -10 in Burnet Texas.
Near Lakeline Mall Dr., Cedar Park, Texas 78613
Check out the Areas We Serve and jobs we are doing by clicking: https://prorefrigerate.com/areas-we-serve/