Check out motor tripping protector. Motor protector maxed out at 1.6A setting. Motor pulling 1.4 RLA. Bad protector. Procure parts. Replace protector and aux switch. Set new protector for 2.2A. Check unit operation. Ran complete cycle no issues on 11/8/23 in Austin Texas.
Near Rock Rose Avenue Austin, Texas 78758
Check out the Areas We Serve and jobs we are doing by clicking: https://prorefrigerate.com/areas-we-serve/