On 11/06/2022 Left pasteurizer slow. Discharge water barley body temp. Sight glass flashing. Low on refrigerant. Add refrigerant to left pasteurizer. Pressures are better. Unit pulled down and cycled off while working on right pasteurizer. Will return with high temp relay on follow up work order on regular hours since this was a weekend service. Add glycol to right pasteurizer. Jump out high temp relay. Turned unit on. Observed unit heat up to 85 C switch over to cooling pulling down to 12 C. Stopped unit so staff can process base mix in Austin Texas.
Near Rock Rose Avenue Austin, Texas
For more information, also Check out the Areas We Serve https://prorefrigerate.com/areas-we-serve/