On 8/25/2023 Checked in with kitchen staff. Looked at French fries’ freezer. Evaporator fans running coil clean no ice. Liquid line hot. Clean condenser. Liquid line proper temperature. Checked thermostat. Checked time clock. Unit has not had taps installed yet. Installed piercing valve checked pressure. Suction a little low. Checked with leak detector. No leaks inside or outside. Cap tube starting to plug up. Replacing cap tube is best option in Austin Texas.
Near Manor Rd Austin, Texas 78722
Check out the Areas We Serve and jobs we are doing by clicking: https://prorefrigerate.com/areas-we-serve/