12/06/2022 Located condenser to roof. Removed condenser, opened lines at evaporator. Cut out old TXV, connected liquid line to distributor tube and soldered. Flushed out lines with Kleen Flush. Ran line set to condenser. Wired in a defrost clock and liquid line solenoid @ the condenser. Replace TXV and thermostat at evaporator. TXV equalizer line snapped off suction header so I had to re do the entire equalizer line in Austin Texas.
Near Double Creek Dr Round Rock, Texas 78664
Check out the Areas We Serve and jobs we are doing by clicking: https://prorefrigerate.com/areas-we-serve/