On 12/29/2022 Ordered and picked up the compressor. Removed old compressor and cleaned condenser outside with water Installed new compressor with new start kit components, new c032s t-cap Then started flushing the lines, I have found that the cap tube was clogged. I had to uninstall it and use RX flush with nitrogen to clean it out. Then I pulled vacuum to 530microns Added 1 lbs. of 134a And have it running until unit hit setpoint of 35° in Austin Texas.
Near N Lexington St. Manor, Texas 78635
Check out the Areas We Serve and jobs we are doing by clicking: https://prorefrigerate.com/areas-we-serve/