On 12/01/2022 Manager stated that freezer still short cycling and they turned it off. I turned it on and tested pressures. Found unit was low in gas in low weather conditions I added 1 lbs of 404 and started a leak search. Found a leak at the suction line service port. Tightened up the service cap and tested with bubbles soap. Freezer is working properly holding head pressure for over 200psi. No other leaks found in Pflugerville Texas.
Near N IH35 Pflugerville, Texas 78660
Check out the Areas We Serve and jobs we are doing by clicking: https://prorefrigerate.com/areas-we-serve/