On 7/21/2023 Checked wiring at coil. Checked wiring at unit. Rewired control wiring from time clock through thermostat and solenoid. From 4 on time clock to thermostat to solenoid. Unit now pumps down and cycles off. Found start cap blown replaced start cap with cap from old compressor. Soldered leak on suction line king valve. Unit operating properly at this time in Marble Falls Texas.
Near Farm to Market Rd 1431 Marble Falls, Texas 78654
Check out the Areas We Serve and jobs we are doing by clicking: https://prorefrigerate.com/areas-we-serve/